## Foam Products

###### Handline Nozzle Auto Water/Foam La 1″

Read More

This nozzle provides a combination fog and straight stream flow. Flowrate and flow pattern can be adjusted without closing the nozzle. Nozzle can be easily open and close with the quick turn handle.

###### Handline Nozzle Auto Water/Foam La 2″

Read More

This nozzle provides a combination fog and straight stream flow. Flowrate and flow pattern can be adjusted without closing the nozzle. Flowrate can be adjusted from 340LPM to 530LPM. Nozzle can be easily open and close with the quick turn handle. This nozzle provides excellent discharge in the application of AFFF and non-protein foam.

Code No. | Material | Finishing | Inlet Size | Flowrate @ 65Psi (4.4 Bar)
--- | --- | --- | --- | ---
FOS005-LA-050-BK | Aluminium Alloy | Natural | 2″ & 2 1/2 Male BSP | 90-119-140-FLUSH GPM
2 1/2″ Male BS336 | 340-450-530-FLUSH LPM

Setting | Flow rate @ 6 Bar | Throwrange @ 6 Bar
--- | --- | ---
JET | 1/2 Spray | Full Spray | JET
90G / 340L | 368 LPM | 372 LPM | 372 LPM | 30m
119G / 450L | 464 LPM | 482 LPM | 494 LPM | 25m
140G / 530L | 520 LPM | 560 LPM | 568 LPM | 25m
FLUSH | 564 LPM | 620 LPM | 620 LPM | 15m

###### Water / Foam Pistol Grip Nozzle (Jet / Fog)

Read More

This nozzle provides a combination fog and straight stream flow. Flowrate and flow pattern can be change without closing the nozzle. It is available in heavy duty bronze construction and also light weight aluminium alloy construction. Flowrate can be adjusted from 150LPM to 460LPM. Nozzle can be easily open and close with the quick quarter turn handle.

This nozzle provides excellent discharge in the application of AFFF and non-protein foam.

Optional aeration foam tube (FOS011-LA-STD-NA) is available to fit on the end of the nozzle to enhance expansion of foam solution and also deliver a longer and heavier foam blanket (expansion rate 8 to 1). It is easily attach and secure to the nozzle.

Code No. | Material | Finishing | Inlet Size | Flowrate | Throwrange @ 65Psi (4.4 Bar)
--- | --- | --- | --- | --- | ---
FOS005-LA-038-BK | Aluminium Alloy | Black | 2 1/2″ Male BS336 | 150-220-350-460 LPM | 22m (JET)
FOS005-GM-038-BK | Copper Alloy | Natural | 2 1/2″ Male BS336 | 40-60-95-125 GPM | 14m (SPRAY)
FOS005-LA-38BGDV | Aluminium Alloy | Black | Bogdanov/GOST | 150-220-350-460 LPM

###### Foam Station Cabinet

Read More

This hose reel station is complete with 1-1/2” x 30M rigid hose, 225L AFFF foam, stainless steel foam concentrate storage tank, 95GPM foam inductor and nozzle. A bypass loop is provided for water or foam discharge. Protection of oil storage installation loading stations, paint and solvent stores.

Code No. | FOS087-MS-STD-RD
Inlet Connection | 1-1/2″ ANSI 125 RF flange
Hose reel construction | Aluminium or Hot Dip Galvanised Mild Steel
Tank Construction | Stainless Steel
Cabinet Construction | Mild steel or Stainless Steel (Upon request)

Standard Features
2 nos (2-1/2”) 65mm x 30m fire hose (Type 1) with Aluminium Alloy BS coupling
140 L AFFF foam in fibre glass tank.
2″ Gate valve
Low expansion foam branch pipe 225LPM
Ø200mm opening hole for foam concentrate filling
225LPM foam inductor adjustable 3% to 6% foam concentrate
Inlet connection: 2″ BSP Male thread

Code No. | FOS089-MS-STD-RD
Dimension | 1500.0mm x 1100.0mm x 500.0mm
Material | Mild steel for cabinet
Thickness | 1.5mm
Installation | Floor Mounted
Capacity | 140 litre foam with Inductor with 2 – 1/2″ x 30m hose Type 1 (2 lengths) and Foam branchpipe
Paint Finish | Epoxy Powder Red

###### Foam Line Proportioner

Read More

- Water flowing through foam line proportioner creates a vacuum which draw foam
  concentrate into the unit to mix with the flowing water.
- Suitable for fixed foam system
- Low cost foam proportioning system
- Connect foam suction inlet to foam storage tank
- Material: Gun Metal
- Inlet 2-1/2″ BSP, Outlet 2-1/2″ BSP
- Suitable for foam spray system and foam hydrant station
- Available with 3% or 6% foam concentration proportioning

Code No. | Flowrate @ 101 Psi (7 Bar)
--- | ---
FOS040-GM-380-RD | 380 LPM
FOS040-GM-570-RD | 570 LPM
FOS040-GM-760-RD | 760 LPM
FOS040-GM-950-RD | 950 LPM
FOS040-GM-1140-RD | 1140 LPM
FOS040-GM-1843-RD | 1893 LPM

###### Low Expansion Foam Branchpipe

Read More

- Material: Aluminium Alloy
- Suitable for AFFF, protein and AR foam
- Available with two flowrates
- Expansion ratio: 7-8
  Inlet: BS 336 Instantaneous male
- Foam branchpipe is available with integral foam inductor and pick up tube

Code No. | Flowrate @ 101 Psi (7 Bar) | Throw Range
--- | --- | ---
FOS003-LA-225-YW | 225 LPM | 18 to 22m
FOS003-LA-450-YW | 450 LPM | 20 to 25m
FOS003-LA-900-YW | 900 LPM | 30 to 40m
FOS008-LA-225-YW | 225 LPM | 18 to 22m
FOS008-LA-450-YW | 450 LPM | 20 to 25m
FOS008-LA-900-YW | 900 LPM | 30 to 40m

###### Portable Foam Inductor

Read More

- Container colour: White (Blue colour container subject to availability)
- Capacity: 20litle
- Inlet : 1″ BSP Male

###### Foam Fire Extinguisher On Trolley EN1866

Read More

- AFFF foam is suitable for class A and B fire and highly effective for flammable liquid fire.
- Trolley unit can be operated by one person and suitable for areas with high risk fire such as industrial facilities
- Material of Cylinder Stainless Steel.

###### Mobile Foam Fire Extinguisher on Trolley

Read More

The foam liquid extinguisher on trolley is highly manoeuvrable and it is suitable for outbreaks of fire that cannot be dealt with by using portable extinguishers. It is effective on flammable liquid fire.

This is a self-contained foam production unit which only requires connection to suitable water supply (minimum water supply required is 180 LPM at 5 bar).

- 2 x 15m 1-3/4″ (45mm) fire hose with Aluminium BS Coupling
- 225 LPM Foam Indcutor with pickup tube
- 225 LPM Low Expansion branchpipe
- Control valve (2″ ball valve)
- 120L AFFF, foam concentrate and fibre glass tank on trolley

Performance Data for FEX161-FG-120-W
Input Pressure at Inductor | Total Water Flow | Foam Produced | Approximate running time (min.) Inductor Setting | Foam Throw from Branchpipe
Bar | Litre/Min | Litre/Min | 3% | 6% | m
5 | 180 | 1800 | 22 | 11 | 14
6 | 197 | 1970 | 20 | 10
7 | 213 | 2130 | 18 | 9 | 17
8 | 228 | 2280 | 17 | 8.5
10 | 255 | 2550 | 16 | 8 | 20

###### Foam Inductor

Read More

- Foam concentrate is drawn through a pick up tube at a preset foam concentrate
  amount and is added into the water stream.
- Available with two flowrates
- Body material: Aluminium Alloy and Gun Metal
- Filters: Stainless Steel
- Foam concentrate rate adjustable foam 1% to 6%. Flexible foam concentrate suction hose.
- Inlet and outlet connection BS 336 Instantaneous

Code No. | Flowrate @ 101 Psi (7 Bar)
--- | ---
FOS004-LA-225-YW | 225 LPM
FOS004-LA-450-YW | 450 LPM
FOS004-GM-225-YW | 225 LPM
FOS004-GM-450-YW | 450 LPM

###### Foam Hose Reel Station

Read More

This hose reel station is complete with 1-1/2″ x 30M rigid hose, 120L AFFF foam, stainless steel foam concentrate storage tank, 95GPM foam inductor and nozzle.A bypass loop is provided for water or foam discharge.

Standard Features

- Inlet connection : 1-1/2″ ANSI 125 RF flange
- Hose reel construction : Aluminium
- Tank Construction : Stainless Steel
- Water/foam pistol grip nozzle
- Non-ferrous piping and fittings
- 120L AFFF foam and concentrate
- 1-1/2″ control valve
- Stainless steel pickup tube
- 100mmØ opening hole for foam concentrate filling
- Adjustable foam concentrate 3% to 6%
- Application:
- Protection of oil storage installation loading stations, paint and solvent stores.

###### Medium Expansion Foam Branchpipe

Read More

- Material: Stainless Steel
- Suitable for AFFF, protein and EP foam
- Available with two flowrates
- Expansion ratio: 50
- Inlet: BS 336 Instantaneous male

Code No. | Flowrate @ 101 Psi (7 Bar) | Throw Range @ 101 Psi (7 Bar)
--- | --- | ---
FOS010-SS-225-YW | 225 LPM @ (7 Bar) | 3 to 8m
FOS010-SS-450-YW | 450 LPM @ (7 Bar) | 4 to 11m

##### 2kg Co2 Fire Extinguisher