## Wet and Dry Riser Systems

###### Fire Hydrant Valve BS 5041

Read More
Specification
Body : Copper Alloy to BS 1982
Handwheel : Grey Cast Iron to BS EN 1561
Inlet : Flanged or BSP screw thread
Outlet : Female instantaneous to BS 336 and other connections
Working Pressure: 15 bar
Manufacture and certified to BS 5041 Part 1*
Nominal size: DN65 2-1/2”, DN50 2″. DN80 3″

Straight Through Valve

Code No. | Inlet Size
--- | ---
DRS107-GM-65BSP* | Male BSP Thread 65mm
DRS107-GM-65NST | Female Screw 65mm-NST
DRS108-GM-65ANSI | C ANSI 150 FF Flange 65mm
DRS108-GM-65PN16* | BS 4504 PN16 65mm
DRS108-GM-65TE | BS 10 Table E Flange 65mm
DRS108-GM-UK80AB | ANSI 150 FF Flange 80mm

Right Angle Valve

Code No. | Inlet Size
--- | ---
DRS105-GM-65BSP* | Male BSP Thread 65mm
DRS106-GM-65TE | BS 10 Table E Flange 65mm
DRS106-GM-65PN16 | BS 4504 PN16 65mm
DRS106-GM-UK65AB | ANSI 150 FF Flange 65mm
DRS106-GM-UK80AB | ANSI 150 FF Flange 80mm

Bib Nose Valve

Code No. | Inlet Size
--- | ---
DRS109-GM-UK65AB | ANSI 150 FF Flange 65mm
DRS109-GM-UKPN16* | BS4504 PN16 65mm
DRS109-GM-UK65MB* | Male BSP Thread 65mm
DRS109-GM-UKTE | BS10 Table E Flange 65mm
DRS109-GM-UK80AB | ANSI 150 FF Flange 80mm

Oblique Valve

Code No. | Inlet Size
--- | ---
DRS097-GM-65BSP* | Male BSP Thread 65mm
DRS098-GM-65ANSI | ANSI 150 FF 65mm
DRS098-GM-65PN16* | BS 4504 PN16 Flange 65mm
DRS098-GM-80ANSI | ANSI 150 FF 80mm
DRS098-GM-65TE | BS 10 Table E Flange 65mm

###### Pressure Regulating Valve ‘E’ Type

Read More

Features

- Suitable for inlet pressure up to 20bar
- Reduced outlet static pressure can be set from 5 to 8bar
- Outlet pressure remain constant with inlet pressure range from 7bar to 20bar
- Pressure test to 30bar
- Minimum Flowrate up to 1400L/M

Code No. | Inlet Size
--- | ---
WRS121-GM-65BSP* | Male BSP Thread 65mm
WRS120-GM-65TE | BS 10 Table E Flange 65mm
WRS120-GM-65ANSI | ANSI 150 Flange 65mm
WRS120-GM-65PN16* | BS 4504 PN16 65mm
WRS120-GM-80ANSI | ANSI 150 FF Flange 80mm

###### India Landing Valve Double Head

Read More

Code No. | Outlet | Inlet
--- | --- | ---
DRS141-GM-100PN16 | 2 1/2″ Female Instantaneous IS: 5290 | 4″ PN16

###### Gate Valve & Fire Brigade Valve

Read More

Gate Valve

Code No. | Inlet Size
--- | ---
DRS120-GM-BSPN16 | BS 4504 PN16 65mm
DRS120-GM-65TE | BS 10 Table E Flange 65mm

Fire Bridgade Valve

Code No. | Inlet Size
--- | ---
DRS110-GM-65BSPT | BSP 65mm male thread

###### 2-way & 4-way Breeching Inlet Specification

Read More

Body | Ductile Iron
Inlet | BS Instantaneous Male Copper Alloy to BS 1982
Outlet | 2 Way Breeching Inlet Flanged 4” table E. BS 10
4 Way Breeching Inlet Flanged 6” table E. BS 10
2 Way Breeching Inlet Flanged 4” table D
2 Way Breeching Inlet Flanged 3” ANSI
Working Pressure | 10 Bar
Testing Pressure | 20 Bar

Code No. | Description | Inlet Size | Outlet Size
--- | --- | --- | ---
DRS095-DI-BSPN16 | 2-way breeching inlet | BS 336 Male | Table E/PN 16
WRS115-DI-BSPN16 | 4-way breeching inlet | BS 336 Male | Table E/PN 16
DRS095-DI-BSPN 16 | 2-way breeching inlet | BS 336 Male | Table D
DRS095-GM-080AN | 2-way breeching inlet | BS 336 Male | 3″ ANSI

###### Air Release Valve

Read More

Code No. | Inlet Connection
--- | ---
WRS104-GM-020-NA | 20mm (3/4″) BSP
WRS104-GM-025-NA | 25mm (1″) BSP

###### Hose Rack Assembly

Read More

Hose rack assembly is located inside the buildings at the wet or dry riser outlet. It features a rack in which hangs the layflat fire hose (30m). An automatic release mechanism allows water to flow through the hose after removal of the hose and nozzle. The rack is available in sizes of 1-1/2″ and 2-1/2″. there are two methods of mounting the hose rack. One is by using a wall bracket and the other is by fixing on to a right angle valve.

###### Double Outlet Standpipe

Read More

Standpipe Shaft | Aluminium alloy to BS 1474
Standpipe Base & Head | Aluminium Alloy to BS 1490 Copper Alloy to BS 1982 Aluminium Alloy or Copper Alloy
Code No. | HYD064-LA-065-NA HHYD064-GM-065-NA HYD064-GM-015-BK*

###### Low Expansion Foam Branchpipe

Read More

- Material: Aluminium Alloy
- Suitable for AFFF, protein and AR foam
- Available with two flowrates
- Expansion ratio: 7-8
- Inlet: BS 336 Instantaneous male
- Foam branchpipe is available with integral foam inductor and pick up tube

Code No. | Flowrate @ 101 Psi (7 Bar) | Throw Range
--- | --- | ---
FOS003-LA-225-YW | 225 LPM | 18 to 22m
FOS003-LA-450-YW | 450 LPM | 20 to 25m
FOS003-LA-900-YW | 900 LPM | 30 to 40m
FOS008-LA-225-YW | 225 LPM | 18 to 22m
FOS008-LA-450-YW | 450 LPM | 20 to 25m
FOS008-LA-900-YW | 900 LPM | 30 to 40m

###### Foam Inductor

Read More

- Foam concentrate is drawn through a pick up tube at a preset foam concentrate
  amount and is added into the water stream.
- Available with two flowrates
- Body material: Aluminium Alloy and Gun Metal
- Filters: Stainless Steel
- Foam concentrate rate adjustable foam 1% to 6%. Flexible foam concentrate suction hose.
- Inlet and outlet connection BS 336 Instantaneous

Code No. | Flowrate @ 101 Psi (7 Bar)
--- | ---
FOS004-LA-225-YW | 225 LPM
FOS004-LA-450-YW | 450 LPM
FOS004-GM-225-YW | 225 LPM
FOS004-GM-450-YW | 450 LPM

##### 2kg Co2 Fire Extinguisher